AC Repair Chandler Arizona and maintenance service provided in the cities of: Mesa, tempe, scottsdale, gilbert, apache junction, gold canyon, queen creek, and phoenix.
At last, experience professional Air Conditioning Services in Chandler at LOW prices!
* A+Rating at the Better Business Bureau.
* No Travel Time Charges.
* No Extra Charge Evenings and weekends.
* Service Call: Just $79.95
* Parts Available For Do-It-Yourselfers.
* One Year Warranty on ALL Work.
* Licensed, Bonded, & Insured For Your Protection!
A/C Tip: Keeping your air conditioning coils clean can prevent future breakdowns, provide lower electric bills, and improve the very air that you breathe. Visit our cleaning-air-conditioning-coils page to learn more.
104 S Pomeroy
Mesa, Arizona 85210
Open 7 days 5am-7pm
Service Call: Customer wanted a phone quote to replace a Trane compressor. After giving her the quote, she went on to say that the previous company wanted four hundred dollars more than what I had quoted and she wanted to schedule the replacement immediately.
Air Conditioning Repair: I replaced the compressor and installed a liquid line dryer filter. The old compressors crankcase heater was too big for the new compressor. I informed the customer of this and told them that I would return and replace it with one that would fit properly at no charge.
Service Call: Customer states that the a/c doesn't blow cool air and is need of service.
A/C Repair: This was a Goodman heat pump and the condenser fan motor wasn't spinning. Upon further inspection, it was found that only one wire of the motor was hooked up to a capacitor of the wrong size. Also, one of the wires that was necessary for the operation of the motor was deliberately cut off by someone. The correct size capacitor was installed and re-wiring of the motor. However, the motor still didn't work. The only choice left was to replace the fan motor. After replacement unit operated normally.
Service Call: Customer says that her house is getting warmer by the minute and there's hardly any air coming out of her vents. I asked her if her air filter was clean (because very dirty air filters can cause icing and restrictive air flow). She stated that she changes the air filters every month. She was then informed to turn the system off at the thermostat, and to turn the fan to the on position. This would help to melt any ice that may be present prior to service.
Upon arrival, it was noticed that a pool of water had collected at the end of condensate drain line and no water was leaking out. This was a good indication that the indoor coil was in fact iced up, melted, and drained. Pressures indicated that unit was low on freon. Customer opted to add some freon versus doing a leak check and repair. Unit operates normally at this time, but with a minor freon leak.
AC Repair Chandler Arizona
Service Technician Calls Cont'd
Customer states that the air blows from the vents but then stops suddenly even though the outside air conditioner keeps running.
Air Conditioning Repair:
When you have this type of symptom with your ac unit the most common types of problems that could cause it are:
After diagnosing this customers particular problem, I simply tightened the connections at the thermostat and the 24v connections at the air handler and the problem went away. Everything else in the system checked out fine.
Although I informed the customer that if the problem persisted, it would mean that the problem is intermittent (something that is difficult to diagnose when the unit is running the way it should) and the next logical approach would be to replace the control board.
Customer says that his air conditioner is blowing room temperature air and that the unit is making a loud noise.
AC Repair Chandler:
This was a split system Goodman air conditioner and the condensing units motor was making a loud noise due to worn out motor bearings. Some of these generic universal motors can be mounted with it's shaft pointed upwards, downwards, or sideways depending on the design of the air conditioners manufacturer. These motors have rubber plugs inserted into holes on one or both sides of the motor and if installing the motor regardless of shaft being up or down, the plugs need to be removed at the bottom of motor for drainage purposes (in case water gets into the motors housing), and the plugs need to be inserted into the top of the motor to keep rain out. This particular motor was installed with the plugs missing from the top portion of the motor which more than likely resulted in a shorter life span for this motor.
Return from AC Repair Chandler to air conditioning phoenix
A/C Handyman - 104 S Pomeroy, Mesa, AZ. 85210
Copyright© 2008- All Rights Reserved
Easy to work with great service
by George Arechiga
I manage 2 duplex units a total of 4 homes in Arizona and when I need service I call the A/C handyman. He is easy to work with and I don't feel like he is over charging me he has very good rates. And he shows up when he says he will. I really like his service.
Honest Air Conditioner Repair
by Ethel Duplisea
Bradley was recommended to me by a family member. It was one of the best reommendations I have received in some time. A/C Handyman is on time, proffesional and charges a fair price. Thank you Bradley.
Quick and Excellent Service
My A/C wasn't blowing cool, so I called at 7:00 am on a Friday. He showed up at 8:30 (when he said he would BTW) the same day! Added freon, and didn't try any hard sell tactics. Would highly recommend his services.
Delivered on his Promises
by John Birch
I saw Bradley's company in a comparison against most all the other Hvac companies in my area... while others sounded good, I was not impressed with what customers wrote about their service and fairness on pricing.... I think Bradley is extremely honest and you really do get pricing that is half of the other HVAC companies... Nice! Bradley is also the owner which I like. Nothing like dealing directly with the person that owns the business that you are buying from!!
by Leah Vega
We have two air conditioning units in our home, and every year before the hot weather hits we like to get our air conditioning units serviced to make sure they are working in the most optimum condition. The gentleman that came out to service our units was very courteous and professional. I will definitely be using this company in the future for all of my a/c service needs.
Fair, Honest, and Responsive
I called Brad early sunday AM. By 10:00 AM, the air was cold and I was relieved not to have a ridiculous bill. I have had some bad experiences with AC companies in the past but his timeliness, friendly manner, and fair prices were a huge relief. Brad's my AC guy from now on... thanks Brad!
Found my AC guy! Thanks
by John Shumway
(Queen Creek, AZ)
I do IT consulting on my own so I thought that there must be smaller companies with hard working honest guys around that do AC work. Google brought up Bradley's web page, and actually read the testimonials and thought I would give him a shot. Bradley came and diagnosed the problem to be a motor, he spent an hour making sure, and returned after obtaining the part and finishing up the other work he had scheduled that day which ended up being 11:00pm to replace it so my family could get some sleep. NO WAY would a large company have come that late, at least not without extreemly heavy fees. Thanks for the fair price and Excellent service!
Quick and good service!
by Joe Andreyka
(Gold Canyon, AZ, USA)
We got fast service when we needed it, and our a/c problems were solved, and our service rep was courteous and dependable.
Thank you! Joe and Janice Andreyka
by Valerie & Don
(Apache Junction, AZ)
Brad had all the parts necessary for fixing our unit quickly. I would highly recommend his services. The charges were very reasonable.
Thank you for your expertise and very Quick Service!
Excellent Service and Knowledge
by Randall Thompson
(La Habra, CA)
I live in California and own a rental in Mesa, Az. I have used Brad as my A/C guy for a few years now because he is always there when I need him and I feel that he is honest and upfront with all details of the job. He knows A/C repair very well and gets right to the problem. Being from out-of-state I feel vulnerable to unreputable servicemen. I feel lucky to have found Brad.
Quality Service That is Reliable and Dependable
by Laura Foster
Brad is the AC expert that I rely on for all repairs and questions. In fact, we are buying a new A/C unit through Brad and he will be installing it this month! I recommend him to all of our friends. He is honest, extremely knowledgeable and reliable. He comes when you need him and you can always bank on what he tells you!
Dependable, Professional Service
by Doug Hersho
Having a rental property in Gilbert Arizona while living in Houston Texas requires reliable contractors that you can depend on for servicing. A/C Handyman has filled this requirement beyond expectations. One phone call is all it takes and you know that you don't have to worry about constant followup. Bradley will see to it that the problem is analyzed, reported back to you and repaired as required professionally. I highly recommend their service.